[RE-wrenches] Battery Monitor for Li
Allan at sindelarsolar.com
Fri Sep 2 12:29:54 PDT 2022
Matt, you didn't indicate whether this is a TM2020 or a newer TM-2030.
The steps are the same, so it shouldn't matter.
Set the charge efficiency to 99%. Set the voltage to a few tenths of a
volt below the Simpliphi's BMS setpoint.
Set the amps to off.
Make sure that P01 for auto reset is on.
Should work fine.
On 9/2/2022 12:43 PM, Kirk Herander via RE-wrenches wrote:
> I’ve never installed simplify batteries. Do they make their own state
> of charge monitor?
> The trimetric has a perimeter called charge efficiency % You can tweak
> that to get it to match the any benchmark more closely.
> Also the trimetric should be reset to full on a regular basis, When
> you have confidence the batteries are full. All trimetrics drift off
> over time, especially given the unique charge characteristics of
> lithium-ion’s versus lead acid batteries.
> On Fri, Sep 2, 2022 at 2:32 PM Matt Sherald via RE-wrenches
> <re-wrenches at lists.re-wrenches.org> wrote:
> Hello Friends,
> I have an off-grid customer for whom I recently installed some
> SimpliPhi 3.8kW batteries. This is an older system and it has a
> Trimetric battery monitor that the homeowners have used for years
> to keep an eye on their battery bank.
> The SimpliPhi batteries appear to be working fine at the site, but
> the homeowners feel uneasy b/c the Trimetric is reporting that
> they are finishing each charging cycle with an amp-hour deficit.
> The voltage of the SimpliPhi batteries indicate that they are
> getting fully charged and are doing so fairly early in the AM
> (solar is the primary power source).
> I've spoken with SimpliPhi tech folks and their hunch is that the
> Trimetric is not reporting correctly. They suggested that a
> Victron BMV-712 would be more accurate at tracking Percent Full
> Do you folks think that the Victron is better at counting Ah
> in/out for Li batteries? Or is the Trimetric adequate - do I
> maybe just need to adjust the settings?
> Anyway, the implication that the Victron BMV was better at
> monitoring Li batteries has me curious and I will enjoy hearing
> what the group thinks.
> Thanks for your time!
> Matt Sherald
> PIMBY Energy, LLC
> www.getpimby.blogspot.com <http://www.getpimby.blogspot.com>
> www.getpimby.com <http://www.getpimby.com>
allan at sindelarsolar.com <mailto:allan at sindelarsolar.com>
New Mexico EE98J Journeyman Electrician
Founder (Retired), Positive Energy, Inc.
Founder (Retired), Sindelar Solar
*505 780-2738 cell*
-------------- next part --------------
An HTML attachment was scrubbed...
More information about the RE-wrenches