

If you just have that one inverter, then go with the 40A breaker, the surge will not be an issue as the breaker is designed for that. The inspector may want to see a bolt-on/down breaker or some type of retainer and this can be a hassle. W/o seeing what you have to work w/and you want that 60A for some reason then simply do a tap between the Meter and the 200A Main. Put a 60A fused disco in there and it's a done deal for under a $100, including taps. Use a Burndy or Polaris.
Good luck,
-jeff


>From the Solar, Wind and Hydro powered office of Jeff Oldham



________________________________________________________________________
Try Juno Platinum for Free! Then, only $9.95/month!
Unlimited Internet Access with 1GB of Email Storage.
Visit http://www.juno.com/value to sign up today!

[Non-text portions of this message have been removed]


- - - -
To send a message: RE-wrenches@topica.com

Archive of previous messages: http://lists.topica.com/lists/RE-wrenches/read

List rules & how to change your email address: www.mrsharkey.com/wrenches/etiquette.php

Check out participant bios: www.mrsharkey.com/wrenches/

Hosted by Home Power magazine

Moderator: michael.welch@homepower.com
--^----------------------------------------------------------------
This email was sent to: michael.welch@homepower.com

EASY UNSUBSCRIBE click here: http://topica.com/u/?bz8Qcs.bz9JC9.bWljaGFl
Or send an email to: RE-wrenches-unsubscribe@topica.com

For Topica's complete suite of email marketing solutions visit:
http://www.topica.com/?p=TEXFOOTER
--^----------------------------------------------------------------




